What would you like to do?
The incoming three phase supply connects to the starter terminals L1, L2, and L3. The out going voltage to the motor connects to the starter terminals T1, T2, and T3. If the motor turns the wrong way interchange any two of the T terminal wires at the motor.
3 people found this useful
Was this answer useful?
Thanks for the feedback!
A CONTACTOR SHOULD NOT BE USED TO START A 3-PHASE MOTOR unless there is some sort of motor protection in series with it. You would need a 3-phase contactor and just conn…ect each phase (1 wire) to each terminal of the line side of the contactor, and the 3 wires to the load side. 3 wires on the line side, and 3 wires on the load side.
YES. USE THE NORMAL DIRECT-ON-LINE OR ACROSS-THE-LINE STARTER.
A three phase motor needs 4 connections made to it from the power supply: Phase A, Phase B, Phase C, and Ground. However, many times the motor has 12 labeled leads inside the …connection compartment. Refer to the motor's nameplate to connect the right wires to each other, before connecting them to the power supply. Many times the connections will be made differently for different source voltages. If you do not understand the work well enough to accomplish it yourself properly and safely, don't try it. Consult a professional electrician, as they are proficient enough to do it properly and safely.When working on electrical circuits and equipment, make sure to de-energize the circuit you will be working on. Then test the circuit with a definitive means to make sure it is off (multimeter with metal tipped leads, voltage tester with metal tipped leads, etc., not a non-contact tester, which is non-definitive.)
A 3 phase motor has four connections to the circuit: Phase A, Phase B, Phase C, and Ground. There is no neutral because a neutral is only required for a load that only h…as one hot connection e.g. lighting, receptacles, etc. In the case of a three phase motor, electricity flows into the motor from one phase and out on another phase at any given time. It does not need a neutral. In addition, there are often 12 leads inside the motor's connection housing which can be wired for different supply voltages and/or motor speeds. Refer to the wiring diagram on the nameplate of the motor for this information. ---- If you do not understand the work well enough to accomplish it yourself properly and safely, don't try it. Consult a professional electrician, as they are proficient enough to do it properly and safely. When working on electrical circuits and equipment, make sure to de-energize the circuit you will be working on. Then test the circuit with a definitive means to make sure it is off (multimeter with metal tipped leads, voltage tester with metal tipped leads, etc., not a non-contact tester, which is non-definitive.)
Tree phase reverse forverd wiring diagram
Use VFD to make 3 phase from single phase source.
To terminate a 3 wire wye motor to a 3 phase delta connection you need a 3 phase transformer to convert from delta to wye. Do not lift the common neutral connection…s inside the motor and rewire for delta, because the voltages will be wrong.
Incorrectly connecting a multi-phase motor could potentially cause a huge problem. Inside of the cover where the motor leads reside (we call them 'pigtails') is a diagram of t…he lead connections. They are wired for typically either 230V or 460 Volt AC operation
Yes. Simply connect the motor across any two of the lines. Make sure, however that the line-to-line voltage is the same as the rated voltage of the motor. The reverse does not… apply. Do not connect a 3-phase motor to a single phase supply. Yes, and be aware of a possible "high" leg in your 3ph supply. Some pole transformer conections for 3ph have a high leg delta connection(wild-leg). For instance, 240v 3ph line to ground voltages could read 120v, 208v,120v for the 3 consectutive lines. Of course you want the outer two lines from your panel as the center line should be your "High" leg. For 3ph to 1ph, use a phase converter or build one yourself.
how will you start 3phase inuction motor using star delta stater
Supplying power to a 3-phase motor using a single phase is termed "single phasing", which is, in general, not good for the motor. Depending on the connection, one phase or two… phases will have higher than normal current draw, which could damage these legs. If lightly loaded, the motor might be fine. You need to supply three phase power to a three phase motore for it to operate normally and be able to pull it's specified load. If all you have is a single phase, there are power devices made to give you three phase power from single phase.
No. You need a three phase supply to run a three phase motor. If you only have a one phase supply, you could use an inverter or a motor-generator set, but by the time you did …that, it would have been more cost effective to simply get a one phase motor, or (in the bigger case) upgrade to a three phase supply.
I take it that you are familiar with the configuration of a three phase starter contactor. Incoming lines are L1,L1 and L3. An overload block will be connected to the bottom o…f the contactor. Load lines on the overload block are T1, T2 and T3. Connect two of your supply legs to L1 and L2 on the top of the contactor. From the bottom of overload block terminal T2 supply a jumper to the top of the contactor and connect to terminal T3. Connect the motor to terminals T1 and T3 on the overload block. This configuration will include all of the overload trips into the stop and start circuit. If any of the overload trips open, the motor will become de energized.
The physical internal windings between single phase and three phase motors makes this an impossibility That being said money can make anything happen. Depending on the amount …of money you want to spend to make this happen there is a device on the market called a VFD ( Variable Frequency Drive). On the three phase input terminals you apply your single phase voltage. On the output terminals you connect your three phase motor. When run in this configuration there is an internal switch that has to be changed to let the VFD know that it should be looking for only two lines on the input to be hot. Other wise the VFD thinks that there is a line loss on the three phase input terminals and the unit will not start.