A1: IF it is for a Universal Power supply for electronic equipment, YES it can, as long as the equipment can work with 120V and less than 12 Amps of current. (12 Amps is 80% of a 15 Amp Circuit-That is the Limit of Power through the Wiring). If you need more power (Tim Allen from Tool-Time comes to mind,) then you need to contact an electrician to string new wiring to the outlet.
A2: IF it is for a specific piece of equipment that needs 240V to run, (Stove, Dryer, Welder), then NO, you cannot 'convert' the existing 240V plug.
A3: IF it is for a 'Euro' appliance (Less than 1000 Watts power), IF the frequency of the motor is for 50 Hz, NO, as the speed rating depends on that frequency.
A4: If its for a HDTV or similar appliance, NO, as the appliance is made to work in those countries where the 240 plug works. Adapers are available for the power supply, but for Region DVD players, it will not change the region you are in.
A5: IF it is for an incandescent light fixture, YES, the plug can be converted, as long as the current to the lamp does not exceed the wiring. Typical lamps in North America are designed for 60W lamps, They consume 60W of power when operating, at 120 Volts, and have 1/2 ampere of current in them. 18 Gauge AWG wiring is used for lamp cord as a minimum to handle the current. IF its a EURO lamp, designed for 60W bulbs, at 240V, it will only handle 1/4 Ampere current, and USING a 60W light bulb is TWICE as much as it is designed for. IT would work at 30, but IT IS NOT RATED for 120V service. If your house burned down, the insurance would not cover the fire because the lamp is unapproved for use in North America.
5 different scenarios, 2 will work, 3 will not. Generally you would plug the correct appliance in the correct socket in the correct country of purchase.
Do this electrical work only if you feel confident that you can do it safely. If not then this is the procedure that an electrician would use and you would be able to follow what he is doing. Again an electrician should be your first choice. This answer assumes that the old receptacle was 15 or 20 amps and the new receptacle will be 15 amps. If you consider doing this the first thing is SHUT THE MAIN BREAKER OFF. Use an auxiliary light source to see when working in a dead panel. Always keep in mind an ARC FLASH ACROSS HOT MAINS HAS ENOUGH HEAT TO PEAL THE SKIN OFF OF YOU. Before an explanation of how to do this you should keep in mind that this is for a single receptacle only. If any other receptacles are on the same circuit they will also be changed to 120 volts. That said OK, any 240 volt outlet can be changed to 120 volt by removing the white wire from the 2 pole breaker and inserting it into the neutral bus bar. Remove the other wire (probably black) from the breaker. Remove the 2 pole breaker from the breaker panel. Install two single pole 15 amp breakers into the hole left by the 2 pole breaker. Leave both of these breakers turned off. Connect the black wire that came off of the 2 pole breaker on to one of the new single pole 15 amp breaker. Re install the cover to the electrical panel, this end is finished. Remove the existing 240 volt receptacle and install the new 120 volt receptacle. Materials can be purchased at local building supply store. Remember to take the electrical panel data with you so you have the information for the 2 new breakers. Once you have the receptacle installed, identify on the electrical panel door what the breaker is used for. Leave the unused breaker in the off position. Turn the main breaker back on. Test the new receptacle with a lamp to make sure every thing is OK.
yes, you have two hot lines in a 240 outlet (!!!in North America!!!), disconnect one of them from the breaker box change breaker to a single throw and wire in new outlet
It may not be as simple as above.
Is the old wire heavy enough for the new circuit? You cannot increase the current rating above that of the old circuit, but you can decrease it safely. How many wires are there? If there are 4, you will have an unused hot. If there are 3 you need to switch one hot to be neutral to your new outlet.
Anyways, you need to:
If I understand your question, Can you run a 110 appliance off of a 220 volt outlet? You could by only using one leg of the 220. You may also consider changing the outlet. Put in a regular 110 outlet and capping off one leg of the 220 in the wall box. You still have a neutral and a ground to work with. I read this as the questioner doesn't want to modify the outlet. Check the voltage ratings on the device. Many electronic devices nowadays can havdle 120V or 240V as it is cheaper to manufacture one powersupply and sell it everywhere. If your device is rated for 240V, you can put a 240V plug on it. If it only says 120V, no dice. 240V will burn it up.
Are Danny Devito and Joe Devito related?
How old is Danielle cohn?
40 thousandths equals how many hundredths?
Do mother birds really abandon their chicks if a human touches them?
Are Joe devito and Danny devito related?
Do octopus have nipples?
What is slappy phone number?
What does chongito mean in spanish?
Where is the origin of the Panama hat?
Have you ever crashed a wedding or had your wedding crashed, if so what happened?
How many times did Joe Biden run for president?
What is the world’s oldest soft drink?
How many novels did Charles Dickens write?
What do the colors on America's flag mean?
How did Harry Houdini come up with his stage name?
What is modal fabric?
What does y2m mean in knitting?
What is distinction percentage in ICSE?
BA-28 which is a recommended water-skiing safety practice?
What happened to Simon o'brien's eye?
What is the sequence of the mRNA made from the gene TTACAGGTCCCA?
What is your primary responsibility when other boats are in your area?
Is racing post app suitable for kindle fire Why can't kindle fire find a player when I try to play racing videos replays from Channel 4 Racing app?
What is Alan Hansen doing now?
Copyright © 2020 Multiply Media, LLC. All Rights Reserved. The material on this site can not be reproduced, distributed, transmitted, cached or otherwise used, except with prior written permission of Multiply.