I recommend installing a 120/240V twistlok plug in the box. Then you can plug whatever you want into it. I made a nice distribution panel with 15A breakers for when I want 120V, and 240 can plug in directly. ( I use this method to power my Christmas lights. 2kW. :P)
IF YOU ARE NOT ALREADY SURE YOU CAN DO THIS JOB
SAFELY AND COMPETENTLY
REFER THIS WORK TO QUALIFIED PROFESSIONALS.
If you do this work yourself, always turn off the powerat the breaker box/fuse panel BEFORE you attempt to do any work AND always use a meter or voltage indicator to insure the circuit is, in fact, de-energized.
If there are only 3 wires entering the box, you can't legally do it. You can not use the same wire for a neutral and a protective ground. The 3 wires are the two hot phases and the protective ground.
If there are 4 wires in the box, or if metal conduit provides the protective ground in addition to 3 wires, you can do it, provided the breaker is a double pole breaker. The white wire is the neutral, the bare one is the protective ground
The answer to your question is, yes, many! But really, it depend on where you're living. You can find a Garage Clothing Outlet in Dixie Outlet Mall, if you are looking for a location near Toronto,Canada. Some other Canadian outlet locations are: Marche Centre (in Montreal). To find a location near you, go to the Garage Clothing website and you will find a store locator. Simply type in your city or state/province and the pink-colored star are locations that are outlets and the grey-colored stars are locations that are regular garage store.
Depends on the conductors supplying it and the breaker protecting it. In the US, one quick way to tell is to look at the slots. If there are two parallel slots, it is a 15 amp outlet; if the larger slot (on the left, with ground being down) has a T shape, it is a 20 amp outlet. Also, 15 amp circuits use AWG14 wire, while 20 amp circuits use AWG12 wire.
Garage door openers do not get "wired." They are sold with a standard 3-prong, 120VAC plug that is about two-feet long and plugs into a 15A, 120VAC outlet -- next to the location where the opener is installed. In the absence of a nearby AC outlet, you will need an extension to power you garage door opener. Well power doesn't get wired the wall mount and sensors do get wired use the directions they will tell you where hook the wires on the back of the opener.
All circuits in a kitchen must be 20 amps wired with AWG 12/2 wire. You should have 2 dedicated 20 amp outlet circuits each protected by a GFCI. A dedicated 20 amp circuit for each of these. Dishwasher, refrigerator, garbage disposal, microwave, & lights. That is a total of 7 dedicated 20 amp circuits. This is only the 120 volt circuits and not counting any 240 volt circuits.
How many 3s in 313433535333?
Is it true that one human year is equal to seven dog years?
What is half of 74?
The more you take the more you leave behind what am I?
when There is no requirement to take action to identify and discipline those responsible for the unauthorized disclosure of Controlled Unclassified Information?
What is the setting in the story creole democracy?
Which of the following best describes what is required to be reported to congress?
What makes dr sadao comment 'this man must have extraordinary vitality?
What is a classified data spill or negligent discharge of classified information?
Did Jim Quinn leave occ?
Copyright © 2020 Multiply Media, LLC. All Rights Reserved. The material on this site can not be reproduced, distributed, transmitted, cached or otherwise used, except with prior written permission of Multiply.