Assuming garage is detached less than 80 ft away. You need a 60 AMP double pole breaker for the 200 AMP house panel, and need to have two spare slots. Additionally you should have conduit in running in ground, and have #4/3 W/ground Stranded cable running to the sub panel. This setup will allow for 110V's and a 220V circuit. Connect the two hots, Red/Black to the Breaker on your servicing the panel. Connect the neutral (White) to the Neutral bus bar along with the Ground wire. Sub panel on detached Garage. Attach the White neutral wire to the Neutral ground bar. Attach the ground to the ground bar on the Sub panel. Pull the permits and have it inspected!
If your house has the wires from the meter going straight into your panel box then you tie the neutral and ground to the same busbar. However;
If you havve a disconnect on the outside of your house then you must separate the neutral andground inside the 200 amp panel box. This is usually prevalent on a mobile home or any time the pnel box you are using is fed from another panel or disconnect.
Short answer is Yes. If a garage conversion is carried out you no longer own a link detached house but a semi-detached, indeed if the next house did the same thing you would then live in a terriced house not a link detached
A link detached house is a house that is only joined to another by a garage or just ground flor rom :(((((
A semi detached house has one side of the house that will be attached to another house. A detached house has no shared walls. Most semi detached houses have the garage wall as the shared wall so there is less noise heard from either house.
Adjacent detached properties which do not have a party wall, but which are linked by the garage(s) and so forming a single frontage.
All depends on what type of equipment you are going to operate in the garage. I would suggest you call an electrician. You can connect to your existing 100 amp circuit if there is an empty spot for a breaker.
No. Any connections to the detached garage have to be after the main disconnect of your house panel. You have two options here. You can replace meter with a meter disconnect combo and have the main feed your house and add a breaker to feed the garage or You could install a 400 ap service and place two disconnects at the meter. one for the house and one for the garage. unless you are going to have a serious electrial load in the garage you sould just feed off the panel in the house for cost effectiveness.
A single house is otherwise known as a detached house. A double house is a semi-detached house. Semi detached houses have one shared built wall whereas a detached has space all around it..
No. It can be mentioned in the ad as "detached ?? sq ft garage" and you can include "?? sq ft of land" but not mislead the buyers into thinking the actual house has so much square footage when it is not.
Length x width of the interior edge of the foundation. Also, add the dimension of any attached enclosed garage in the figure. Non-enclosed or detached garage or car port do not apply.
The home and other structures, such as a barn, shed, pool, detached garage, etc. that is located on the land to be sold, unless it is specified not to be sold.
You will need a breaker in your house panel to protect the wire feeders that supply the panel in the garage. The terminology for this setup is called a sub panel. At the garage end you will need a disconnect at that panel as the garage is not attached to the house. You might want to consider a 100 amp combination panel at the garage as it has a built in main disconnect and spaces for 12 or 24 breakers depending on the size of panel you select.
This is called a semi detached house,
A semi-detached house shares one wall with the neighboring house. In America, it's called a duplex.
Attached. In other words, does the house share any walls with another house, like with condos, apartments, duplexes, etc? If not, it is detached.
A semi detached house is one that shares an interior wall with the house directly beside it. The cost to reroof a semi detached house will be around 8,000 dollars, assuming no unexpected problems arise.
A detached house.
Question Needs Clarification!! If you are building a houseand you want the meter mounted on your detached garage to feed the house that is a question that your local utility or electrical inspector would hav to answer as it varies . If you want a meter on your garage that to would have to be answered by your utility as they have requirements about running service wires on residential property. they will probanly allow this as they usually charge more for having the service to a "commercial" building. The bse rate in my locality is twice that of a residential service. And even though it is your personal garage they consider it commercial in most places.
in a semi detached house by Will Wilde
Yes there is a house and there is a garage but you can't to the garage til' you get to world 4. Then you can go in the garage. You just can't go in the house.
house = Haus detached house = Einfamilienhaus semi-detached house = Zweifamilienhaus Flat = Wohnung apartment = Apartment apartment block = Wohnblock bungalow - Bungalow tenement = Mietskaserne
my old house had a small garage, but my new house has a big garage. hope its a good sentence :)
A 'detached' house is not joined to other houses.
the dwelling-detached and the elevated house
If the garage is detached, have a subpanel installed. I would recommend having a professional electrician do this. : IF YOU ARE NOT ALREADY SURE YOU CAN DO THIS JOB : SAFELY AND COMPETENTLY : REFER THIS WORK TO QUALIFIED PROFESSIONALS. : If you do this work yourself, always turn off the power at the breaker box/fuse panel BEFORE you attempt to do any work AND always use an electrician's test meter having metal-tipped probes (not a simple proximity voltage indicator) to insure the circuit is, in fact, de-energized.