First you need to determine if addition of the new breakers will exceed the 200A service under normal operating conditions. If so you will need to go to power company and increase service and put in a larger main panel. If you have the capacity for the extra current you can add a sub-panel and add the breakers there as well as the breakers you will remove from main panel to accommodate the sub-panel breaker. Another way depends on what breakers are in current panel. There are some breakers that can be duplexed in the same space as a single breaker.
8 AWG is typical.
A normal range for a home appliance device usually is wired with a forty amp capacity wire number eight, which is connected to a two-pole forty amp breaker.
Forty acres and a mule is a bad thing, it should not be mentioned.
Yes it should be capitalized.
Around forty kilos.
forty, forty-one, forty-two, forty-three, forty-four, forty-five, forty-six, forty-seven, forty-eight, forty-nine, fifty
It should be MDXL in roman numeralRoman NumeralsIoneVfiveXtenLfiftyCone hundredDfive hundredMone thousand * forty is XL
40 dollars is spelled out 'Forty dollars.'
should be around 3.5 for that price
one hundred forty-five pounds