Want this question answered?
It's "wind chill factor"
Correction of what exactly? You could have filled in the details.
depends on how larger the freezer is and what the materials are used in the freezer and how much of that material is used in the freezer
from some of web address i have got an empirical formulae that density @ 15deg celcius minus (-) 0.0011 is equal to weight reduction factor used for quantifying liquids on mass basis at atmospheric pressure conditions.
end correction in pipe along of the because it is not maximum in the exist of pipe
Yes it changes with the chnage of temperature and you have to calculate the temperature correction factor
Co efficient increasing/degreasing the contact circle is the correction factor in gear.
Power factor correction is a process that has to do with managing the essential traits of electric loads that are used to create a power factor of less than one.
50 ft freezer how size compressor
how can i calculate brsting factor and what may be the bursting factor for corogated pakaging
yes it doesent
Please rephrase your question as I have no clue what you want to know.
Power-factor correction doesn't save energy. Power-factor correction is used to reduce that magnitude of the current drawn from the supply in order to minimise the cross-sectional area of the supply conductors and associated equipment -thus keeping down the cost of the supply circuits which are owned by the supply company. Power-factor correction doesn't apply to homes, but only to larger commercial or industrial premises. The electricity supply company will negotiate a value of power factor for the load, and apply a penalty charge to the customer if his load is not kept within that agreed value.
how to calculate the suction and discharge refrigerant 404 walk in freezer
The only common factor is 3 * * * * * Correction: the only non-trivial factor is 3. Remember that 1 is also a common factor.
using vienna rectifier
I'm not sure I've ever seen an induction motor used to correct power factor; it is usually the induction motors that are causing the poor power factor. "Power factor correction" is usually accomplished by adding capacitors to the system to counteract the inductance of large motors.