Kvar is equal to what?
kVA is the unit for apparent power. Apparent power consists of active and reactive power. Active power is the share of the apparent power which transmits energy from the source (generator) to the user. Reactive power is the share of the apparent power which represents a useless oscillation of energy from the source to the user and back again. It occurs when on account of some »inertia« in the system there is a phase shift between voltage and current. This means that the current does not change polarity synchronous with the voltage. But the heat generated in a winding as well as the eddy current losses generated in a transformer core depend on the current only, regardless of whether it aligns with the voltage or not. Therefore the heat is always proportional to the square of the current amplitude, irrespective of the phase angle (the shift between voltage and current). So a transformer has to be rated (and selected) by apparent power. Answer We define "complex power" as voltage times current (V*I), and thus the unit for power is the Volt-Amp (VA). When a circuit contains non-resistive elements (such as transformers), there is a component of power called "reactive power", which is power that is transmitted as a result of energy stored in inductors and capacitors. Reactive power does no useful work. Complex power is the sum of reactive power and real power (power which does work). When only real power is considered, the unit of power is the Watt. Transformers are rated in VA and not W because heat generated by electricity flowing through a conductor is proportional to the current flowing through the conductor. Although reactive power does no work, the current exists nonetheless and must be accounted for when selecting the proper sized wiring.
35 people found this useful
Answer . KVAR Kilovolt-Ampere Reactive. KVAR Kilovolt-Ampere-Reactance. Acronym Definition . Formular for calculation of kvar.
Kvar = Kilo Volt Amp Reactance.
The reverse KVAR relay protects a generator from a loss of excitation. When the excitation system is lost, reactive power will flow from the system back into the generator. Wh…en this happens, induced currents at twice the system frequency will flow in the rotor windings and rotor structure.
Kvar stands for killo volt amp reactance.
420 micro farad=1 kvar
KVAR is reactive power only; KVA is the vector sum of KVAR and KW KVA^2 = KVAR^2 + KW^2
KVA into KVAR
Electrical power absorbed by the load is a combination of real power as a heat ( I2R) and is measured in KW, but the second port of energy consumed is in the form of imaginary… power ( for inductive and capacitive loads ) like a motors , compressors and is measured in KVAr .
kvar = kva*sin@
1 kvar= how much watts
KVA=â (KVAR 2 + KW 2 ) So, KVAR = â(KVA 2 - KW 2 ) We know KW = KVA cos Î¦ => KVAR = â(KVA 2 - KVA 2 cos 2 Î¦ ) = âKVA 2 (1- cos 2 Î¦) = â…KVA 2 (sin 2 Î¦) = KVA sinÎ¦
Capacitors designed to be used for power-factor correction are rated in reactive volt amperes, rather than in farads. The reason for this is that in order to determine the …necessary correction, a load's existing reactive volt amperes is first calculated, then the reactive volt amperes of the capacitor must be determined in order to achieve the required value of power factor. In other words, the capacitance (in farads) of the capacitor is irrelevant to the calculation.
KVA = KW + jKVAR KVA is full power, which includes the real power component (watts, or kW), and the reactive component (VARs, or kVAR).
There are various ways in which you can determine the reactive power (in reactive volt amperes) of a load. From the practical point of view, you can use a voltmeter and an a…mmeter and use the product of their readings to determine the apparent power (in volt amperes) of the load, and a wattmeter to determine the true power (in watts) of the load, then find the vectorial difference: (reactive power) 2 =(apparent power) 2 -(true power) 2
kvar can be calculated as follows the a product KVA andt the sineof the angle between the KVA and KW.