What would you like to do?
Cellular respiration sometimes is referred to as aerobic respiration, meaning that it occurs in the presence of oxygen, and is not an anaerobic process. Glycolysis …is one of the processes in cellular respiration. In the final steps of glycolysis, two hydrogen atoms are removed from each three-carbon compound by bonding to free-floating oxygen atoms in the cytoplasm to form water.
When oxygen supplies cannot be kept up and the oxidative metabolism cannot produce all the ATP required, there is a switch to processes that break down glucose and glycogen to… lactic acid which diffuses into the blood stream. Creatine phosphate is a substance that aids in the formation of ATP rapidly. Creatine phosphate + ADP ATP + creatine
Gases like methane
Hi, A typical gas system comprises the digester cover, pressure and vacuum relief devices, water trap, flame trap, pressure regulator, gas meter, check valve, press…ure gauges, waste gas burner and a gas holder. Mixing of digesters by means of gas re-circulation requires a compressor. The digester is covered to contain odours, maintain temperature, keeps air out and to collect the gas. Fixed covers are more usual than floating covers. During normal operation, there is a space for gas collection between the cover and the liquid surface of the digester contents. The cover of a digester has certain unique features that the operating staff must be aware of, for example, how the variation in pressure and the level inside the digester may affect the cover. The biggest danger associated with the operation of fixed cover digesters occurs when the pressure relief device mounted on top of the digester fails or the sludge overflow line blocks and the liquid level in the digester continues to rise. In such a situation, the excess gas pressure inside the digester can exceed the maximum design pressure and damage the cover or its mountings. Fixed covers can also be damaged by excess negative pressure (vacuum) or if the rate of waste sludge withdrawal exceeds the feed rate or the vacuum relief device fails. The function of the pressure relief device is to allow pressure that exceeds a safe level to escape from the digester. The manufacturer's specifications should provide the following information to enable the operating staff to control the gas system safely. (a) The system's normal operating pressure (mm water gauge). (b) The pressure at which the pressure relief device should operate. (c) The rated gas flow capacity of the pipes. A gas system generally comprises three pressure relief devices; one mounted on the cover of the digester, one on the gas holder and one situated at the end of the gas line before the gas burner. This device releases gas to the waste gas burner before the design gas pressure of the digester cover is reached. The vacuum relief device functions in the opposite manner to the pressure relief device and allows air to enter the digester in the event of the waste sludge being withdrawn too rapidly. Air should not, under normal conditions, be allowed to enter the digester because a mixture of air and methane is potentially highly explosive. Gas leaving the digester is almost saturated with water vapour. As the gas cools, the water vapour condenses causing problems. The problem is more severe when digesters are heated. To solve the problem it is essential to remove as much of the moisture as possible before the gas comes into contact with the gas system devices. For this reason, water traps should be located as close to the digester as possible. All piping should be sloped a minimum of 1% towards the water trap, which should be situated at a low point in the gas line. Flame traps are emergency devices installed in gas lines to prevent flames travelling back up the gas line (flashback) and reaching the digester. The flame trap generally consists of a box filled with stone or a metal grid. If a flame develops in the gas line, the temperature of the flame is reduced below the ignition point as it passes through the trap and the flame is extinguished. Pressure regulators are used when a lower pressure than the system operating pressure, is required for a specific device such as a boiler water heater or incinerator. Regulators maintain a constant gas pressure at the point of use The rate of gas production is probably the most sensitive process control indicator at the disposal of the operating staff. Gas meters should be regularly serviced so as to give accurate and reliable gas readings. Every effort should be made to have the gas meter calibrated every six months. Check valves (non-return valves) are installed in the gas line to allow gas flow in one direction only i.e. out of the digester. Gas pressure gauges indicate the pressure in the gas system and assist in locating any blockages in the line. If a blockage occurs, a pressure reading downstream will register a lower pressure than that of a gauge upstream. The pressure relief device at the waste gas burner safely flares excess gas to the atmosphere and thus reduces the potential for a dangerous accumulation of gas in the system. Many anaerobic digestion waste treatment plants have a means of storing excess gas. This can be in the form of either a floating roof on the digester or a separate gasholder. A mixture of biogas and air can be explosive. Methane gas in concentrations of between 5% and 15% in air by volume is explosive. Operating staff on waste treatment plants should ensure that no air is allowed to enter the digester or gasholder. All piping and equipment must be sealed properly to prevent gas from escaping to the outside. There must be no smoking and all electrical installations, including light switches, torches etc must be of the explosion-proof type, as the smallest spark could ignite escaped gases. Srinivas kasulla 09869179601 MUMBAI
To break down biodegradable materials. It is used for industrial or domestic purposes to manage biodegradable waste. It doesn't require oxygen.
It occurs in the absence of oxygen. With oxygen = aerobic Without = anaerobic
5000065 wings 5000065 wings
The process of glycolysis. Also known as fermentation.
Anaerobic respiration results from the presence of oxygen. Fuel molecules get broken down and release biochemical energy that comes into contact with the oxygen.
yes, but it requires cardon dioxide
It is the metabolic process that requires the use of oxygen to generate energy
· An anaerobic process It is the metabolic process that requires no oxygen to generate energy for example respiration in the absence of O2 i…s called anaerobic respiration.
Fermentation occurs after glycolysis.
An Anaerobic process is one which takes place without Oxygen being present
The bacterias needed to digest the organic materials and transform it into methane gas only thrives in anaerobic conditions, this means without the presence of air. In fact th…is is what makes bio-digesters good when dealing with waste excrements, because the bacterias don't survive if exposed to air.