No! At this time I wouldn't have less than a 200 amp service for a 3 bedroom house. Keep in mind just because there is a place to plug "stuff" into doesn't mean there is enough capacity in the wiring to handle the load. Please call an electrician. The Fire Department call would be much more expensive.
Blown fuse or circuit breaker. Wires loose on another outlet in that run feeding that bedroom's outlets.
Technically, they can be on a 15 amp breaker when you use 15 amp outlets. There is a difference. Be sure to check your local code (just call the city building department and tell them you have a code question). some cities require the bedroom outlets to be on an arc-fault breaker.
Depends on what the outlets are controlling, size of the wire, and size of the breaker.
Depends on the size wire used in the circuit. If you wired the circuit with AWG #12 wire on a 20 amp breaker then you can install no more than 12 outlets. If you wired it with AWG #14 wire on a 15 amp breaker then install no more than 9 outlets. This is assuming only outlets are on the circuit and nothing else.
Two 20 Amp circuits with the outlets staggered so a different circuit is on two adjacent outlets. Should be GFCI protected.
Your home electrical wall outlets current capacity is governed by the breaker that feeds that circuit. In most home situations the wall receptacles are fed with a 15 amp breaker. Dedicated outlets could have a higher ampacity as they are installed for specific appliances or devices. To check your circuit, plug a lamp into the outlet. Start flipping the breakers off. When the lamp goes out that is the breaker for that circuit. Look on the handle of the breaker and it will tell you the capacity of that particular circuit.
Wires could be disconnected from the main fuse box. Check to see if you have any Ground Fault Outlets installed and ensure that all have been reset. It sounds like they may all be on one circuit and if so, You need to check that all outlets nad light fixtures have good connections and are tight. Its possible that you have a GFI outlet in bathroom that is tripped or is bad the bedroom outlets are possibly wired to same circuit It just may be that the fault that tripped the breaker also broke the circuit to the other points. Look into the boxes of the outlets and switches. If there was a fault you may see carbon where an arc broke a wire to the remaining points in the string.
It would be quite unusual to have a single 60 amp circuit with outlets and lights. You would have to use very heavy wire to each light and outlet. Typical lighting circuits would be protected by 15 amp breaker and a circuit with general purpose receptacles would have a 20 amp breaker. A typical lighting circuit might have 10 to 12 fixtures and receptacle circuit might have 8 outlets. If you don't know how to size a circuit get an electrician.
No. The breaker must protect the circuit components such as wiring, outlets and switches that are connected to the breaker. Therefore if you have a 30 amp circuit as dictated by its components you need to protect it with a 30 amp or less breaker.
The breaker panel. Breakers are placed in series with all outlets.
Somewhere you have a loose or broken connection.
A GFCI receptacle can pass it's "protection" to other outlets wired from it. If the GFCI trips, all outlets wired from it will "trip" also. A GFCI tripping will not necessarily trip the circuit breaker in the service panel.
For the 120 volt outlets on the wall use a 20 amp breaker wired with AWG #12 wire. The circuit must be GFCI protected. Any 240 volt outlets must be wired according to what they will be powering.
There are tow places to put a Ground Fault Circuit Interrupter. There is a GFCI breaker which would be installed in a breaker box and a GFCI outlet that can be installed anywhere. Most GFCI outlets allow you to connect regular outlets to the GFCI and those outlets will also be protected.
Go to your distribution panel and shut off the breaker that you think is the circuit in question. If the circuit becomes de-energized then the breaker you just turned off feeds that circuit. Look on the handle of the breaker and the number you see is the amperage of that circuit. <<>> Determination of a 15 or 20 Ampere circuit is normally indicated by a combination of a 20A breaker and a 20A dedicated outlet. A 15A circuit normally has multiple outlets; not typical in a 20A circuit.
Kitchen outlets are rated at 20 amps and only dedicated for the kitchen. code states that there must be two 20 amp circuits supplying kitchen small appliances. bedroom outlets are fed by a 15 amp circuit most likely and that circuit is most likely feeding two rooms or so.
its an overload on the circuit breaker the 3 outlets are on.. many times groups of outlets are on different circuit breakers.. even though they are in the same room... especially if some are on a gfi outlet
In the United States and in commercial and industrial installations a 20 amp circuit may have 13 outlets, a 15 amp breaker may have 10. In a home there is no limit except common sense. I wouldn't put more than 2 rooms on a circuit. This limits how much goes off when a breaker trips, especially since in homes very often your lights and outlets share circuits.
first be sure to reset the breaker handle to the off position. When a breaker trips the handle goes to a neutral position. After resetting the handle turn it tothe on position. If it trips again there is a short in the circuit. Find out which outlets are not workingand unplug anything that is currently plugged in to the outlets. Reset the breaker and turn it to the on position,if it trips again call a qualified electrician.
Really depends on the load you are going to have on this circuit. But a general rule of thumb for a bedroom, living room, dining room is no more than 13 outlet on a 20 amp circuit.120 volts x 20 amps = 24002400 / 180 volts = 13.333 outletsI personally never put more than 12 on a 20 amp circuit.
A "dedicated" circuit is one to which only one device is or can be connected; therefore the circuit is "dedicated" to the device. A NON dedicated circuit will therefore be one to which multiple devices can connect, such as the wall outlets in your home. Multiple wall outlets are connected to a common circuit breaker, making that an example of a non-dedicated circuit.
You should install no more than 9 outlets. If you add a 75 watt light then install no more than 8 outlets and that 1 light.
The only determining factor is the size of the circuit breaker that you will be using. If the garage circuit will be protected with a 15 Amp breaker, you may use a 14 AWG wire. If the circuit will be protected with a 20 amp breaker, you must use a 12 AWG wire. Note too that garage outlets should be protected with a GFCI breaker or outlet. If you have any concerns regarding your ability to adequately design and install the garage outlets, please, for your own safety, contact a local electrician.
Depends on the breaker. If the load at the outlets is unknown then the standard rules of 80% apply. You can only load a circuit 80% of it's maximum value. For instance, if you're connecting your GFCI outlets to a 15 amp breaker you can only have a maximum of 12 outlets. If it's a 20 Amp breaker then you're allowed up to 16 outlets and so on. In the US, you are limited to 13 receptacles on a 20 amp circuit and 10 receptacles on a 15 amp circuit in commercial or industrial installations. Any or all of these can be gfci-protected. You can install one gfci, the first one from the panel, and protect any or all the others from that one.
According to code, use a 15 amp breaker if you're using 14 GA wire or a 20 amp breaker if you're using 12 GA wire. Another question to ask yourself before deciding on the size of the circuit, how many outlets will you be using, and are you anticipating any special electrical needs? Contact an electrician for assistance with these and any other electrical questions.