Job Training and Career Qualifications
Waves Vibrations and Oscillations
Fire Prevention and Protection
What are some examples of light hazard occupancies per NFPA 13?
Is church considered nfpa light hazard?
Probably not. NFPA 1 "Hazard of Contents" are defined as High (with 5 levels), Ordinary or Low. The only occupancies that have "low" rating are those primarily for storage of non-combustibles. A church is primarily an assembly occupancy and could not be rated as "low hazard", based upon the risks to numerous human occupants. Types of occupancies other than "storage", even if incidentally storing non-combustibles, would qualify as an "ordinary" hazard, under the theory that some combustible materials will be introduced or hazardous operations conducted, or some psychological factor introduced in case of any fire or other emergency, thus requiring at least "ordinary" fire prevention and means of egress.
Asked in Job Training and Career Qualifications, Hazardous Materials Training, Fire Prevention and Protection
What is the highest degree of a hazard identified in the diamond on the NFPA placard?
What is the NFPA handbook?
There are several NFPA handbooks, including Fire Protection Handbook® NFPA 1: Fire Code Handbook NFPA 13: Automatic Sprinkler Systems Handbook NFPA 13D and NFPA 13R: Automatic Sprinkler Systems for Residential Occupancies Handbook, NFPA 20: Stationary Fire Pumps Handbook NFPA 25: Water-Based Fire Protection Systems Handbook NFPA 30 and NFPA 30A: Flammable and Combustible Liquids Code Handbook NFPA 54: National Fuel Gas Code Handbook NFPA 58: LP-Gas Code Handbook National Electrical Code® Handbook NFPA 72® National Fire Alarm and Signaling Code Handbook NFPA 101®: Life Safety Code® Handbook not to mention several manuals, such as Fire and Life Safety Inspection Manual Nursing homes - NFPA Fire and Life Safety Inspection Manual
Asked in Insurance, Fire Prevention and Protection
Is it mandatory to enforce NFPA 13 for insurance?
NFPA 13 only applies to specific types of occupancies and the requirements for enforcement would depend upon the "authority having jurisdiction", local ordinances, and state fire codes. Compliance with such codes is frequently a pre-requisite for obtaining insurance. On the other hand, other facilities may have different requirements (e.g., NFPA 13D or NFPA 13R), or the code may modify the NFPA 13 or NFPA 25 requirements (e.g., NFPA 101 chapter 33 modifications for NFPA 13R in "existing residential board and care facilities"). Your local fire marshal and insurance company will help you with specific requirements.
What are the nfpa hazard diamond rating for solvent?
What do the areas of the NFPA 704 markings indicate?
What NFPA standard addresses fire inspections?
There are over 360 NFPA codes and standards, which provide the basis for inspection under various circumstances. NFPA 1031 addresses the professional qualifications of those who carry out fire inspections and plans reviews. Locally enacted statutes and ordinances often adopt the Life Safety Code and National Fire Code (or equivalent) as the legal requirements for fire inspections. Individual sections of those codes would be the source of the inspection requirements pertinent to a particular type of occupancy or hazard, with reference to the general requirements for all hazards and specific other codes and standards for particular situations. For example, Life Safety Code (NFPA 101) Chapter 15 contains the "life safety" requirements for "existing educational occupancies" with reference to Chapter 9 for fire protection equipment, which references NFPA 10, the standard for fire extinguishers, which references Underwriter's Laboratories and other industrial standards for manufacturing and testing the actual devices. Similarly, NFPA 1, the National Fire Code, contains fire prevention requirements for all sorts of hazards and occupancies, with reference to other codes and standards for specific criteria.
Asked in Hazardous Materials Training
What NFPA 704 marking system color indicates a health hazard?
What color is a fire hazard in the NFPA 704 marking system?
NFPA 704 Hazmat color codes:blue -- health hazard (4 being deadly)red -- fire hazard (4 being flash point below 73 F)yellow -- reactivity (4 may detonate) andwhite -- specific hazard (no water, radioactive, acid, alkali, corrosive, oxidizer)Read more: What_does_the_National_Fire_Protection_Association_704_blue_color_code_stand_for
Asked in Fire Prevention and Protection
Sprinkler coverage area for extra hazard heads?
Extra hazard occupancies require densities of either 0.30 gpm/sq ft or 0.40 gpm/sq ft, for which the maximum head layout is 100 sq ft per NFPA 13. There are some sprinkler heads in the market that allow coverages up to 196 sq ft with a special listing. Tyco EC-25 and EC-17, and Reliable MBEC-14 are some of the heads that can be used with certain restrictions.
Asked in Technology
What the function of the tamper switch in a fire sprinkler system?
Is fire extinguisher is needed for a small room?
Fire extinguishers are required according to local, state or federal fire codes, as may apply to the particular structure. Some "small rooms" may need their own extinguishers. Under the NFPA 1 Fire Code, nearly all types of occupancies other than one- and two-family dwellings are required to have at least one portable fire extinguisher, even if there are fire alarms, fire sprinklers and "fire-proof" construction. NFPA 1 (2009): Table 13.6.2 Portable Fire Extinguishers Required (by occupancy use). For example: There must be no less than one fire extinguisher within 75 feet of any Class A Hazard and within 30 or 50 feet of any Class B hazard (depending upon size of extinguisher and type of hazard). NFPA 1 (2009): Table 184.108.40.206.1.1 Fire Extinguisher Size and Placement for Class A Hazards and Table 220.127.116.11.1.1. for Class B Hazards.
What are the NFPA hazard diamond ratings for Diesel fuel?
Asked in Hazardous Materials Training
What does the code OXY in the bottom white quadrant of a label conforming to NFPA 704 indicates?
Is the NFPA 704M system a federal law?
NFPA codes are enacted selectively, in possibly amended forms, by each state. Similarly, different federal agencies may adopt their own standards or use NFPA standards. For example, OSHA has its own Hazard Communication System (HCS) that is completely different from NFPA 704, using pictograms, being phased in as of December 2013. USDOT also has its own standard for HAZMAT labels (e.g., orange, red, green, yellow, striped, with code numbers and code symbols).